| Harald||2014-07-24 02:35:55|
800 x 534, 59 кБ110 kV/20 kV-substation at Nagold, Germany
| Harald||2014-07-23 02:40:12|
800 x 600, 23 кБThe mast of Thurnau transmitter with all guys. The black dots in the guys are the insulators, the red balls serve just for aircraft warning.
| Harald||2014-07-23 02:34:17|
800 x 534, 82 кБThe guys of the first and second guy level of Thurnau transmitter are divided by insulators in conventional manner as the upmost guy screens it from high static charges during thunder storms. So close to their common anchor basement, there is no coil for grounding.
| Harald||2014-07-23 02:28:09|
800 x 534, 94 кБAn other view of the guy anchor of the upmost guy level of Thurnau transmitter and the coil used to ground the guy
| Harald||2014-07-23 02:22:48|
800 x 1200, 153 кБThe guy of the upmost level of Thurnau transmitter is divided by an insulator. However, there is still the possibility that the rest of the guy disturbs too much the radiation of the transmitter. In order to solve this problem, there are two ways:
1.) Dividing the guy by further insulators
2.) Grounding the guy with a coil with an inductivity chosen in a way that the disturbance by the guy is very small.
Way 1 has the disadvantage that especially at very tall masts at certain weather conditions high voltages at the guy sections may occur, requiring insulators designed for much higher voltages than that produced by the transmitter and voltage arresters bridging the insulators, which are expensive to maintain.
At Thurnau transmitter for the upmost guy level, way 2 was chosen. The coil for grounding the guy is situated close to the anchor basement.
| Harald||2014-07-23 02:04:55|
800 x 1200, 124 кБAn other view on the base of the mast of Thurnau transmitter
| Harald||2014-07-23 02:00:18|
800 x 534, 73 кБBasement of the mast of Thurnau transmitter. One can see the huge insulator on which it stands and the feeder line used for feeding it with the radio power to be radiated. The coil in the line prevents too fast voltage rises, which can occur in case of a lightning strike and damage the transmitter.
| Harald||2014-07-23 01:53:48|
800 x 1200, 62 кБClose view up the mast of Thurnau transmitter. The guys of the first and second level are attached with insulators at the mast, while that of the upmost are not. The insulator for dividing one of the upmost guys is visible on the picture.
| Harald||2014-07-23 01:48:02|
800 x 1200, 48 кБThurnau transmitter is a mediumwave transmitter working on 549 kHz with 100 kW south of Thurnau, a town in Northern Bavaria, Germany. It uses as antenna a 240 metres high guyed mast insulated against ground. The mast is electrically enlengthened as the guys of the upper level are connected directly toward the mast and divided by an intermediate insulator.
| Harald||2014-07-18 03:06:46|
800 x 1200, 73 кБErection of a new powerline tower near Aldingen, Germany
| Harald||2014-07-17 15:59:07|
800 x 1200, 135 кБClose look at an anchor tower of the shielding wires over motorway A8 at Heusweiler
| Harald||2014-07-17 15:55:24|
800 x 534, 75 кБThe shielding grid over motorway A8 at Heusweiler
| Harald||2014-07-17 15:51:13|
800 x 534, 60 кБBasement of the 50 metres mast of Heusweiler transmitter. Unfortunately the basement insulator is poorly visible through the fence.
| Harald||2014-07-17 15:47:18|
800 x 1200, 74 кБThe 50 metres high mast of Heusweiler transmitter, used for broadcasting on 1179 kHz. It is insulated against ground.
| Harald||2014-07-17 15:43:37|
800 x 534, 39 кБBasement of the 120 metres mast of Heusweiler transmitter with the cage antenna
| Harald||2014-07-17 15:40:51|
800 x 1200, 83 кБThe lower part of the 120 metres high mast of Heusweiler transmitter with the cage antenna
| Harald||2014-07-17 15:36:46|
800 x 1200, 61 кБA further view on the two 120 metres high masts.
| Harald||2014-07-17 15:32:49|
800 x 1200, 75 кБThe two 120 metres of Heusweiler transmitter. The mast on the right is a mast radiator insulated against ground, the mast on the left is equipped with a cage antenna on the lower part similiar to the ARRT-antennas realized in Ukraine.
The wires of the cage antenna, which are triple conductors are fixed with insulators designed for 110 kV at the two upper rings, which are fixed at the mast. The lowest ring is the collector of the cage antenna and fixed with insulators at three steel poles.
| Harald||2014-07-17 15:29:12|
800 x 1200, 70 кБThe two 120 metres of Heusweiler transmitter. The mast on the right is a mast radiator insulated against ground, the mast on the left is equipped with a cage antenna on the lower part similiar to the ARRT-antennas realized in Ukraine.
The wires of the cage antenna, which are triple conductors are fixed with insulators designed for 110 kV at the two upper rings, which are fixed at the mast. The lowest ring is the collector of the cage antenna and fixed with insulators at three steel poles. The wires in the foreground belong to the shielding grid of nearby motorway A8.
| Harald||2014-07-17 15:16:23|
800 x 534, 29 кБHeusweiler transmitter is a very powerful mediumwave broadcasting station at Heusweiler north of Saarbrücken in Germany. It actually broadcasts on 1422 kHz with 400 kW and 1179 kHz with 10 kW.
Until Mid of 1990ies the transmitter used a power of 1200 kW at daytime. The heat generated by the transmitter was used for heating a ( now closed) indoor swimming pool!
Over the nearby motorway shielding wires were spun, in order to protect vehicles from high power transmitter radiation. Interestingly a bridge over the motorway open for cars is not shielded.
Heusweiler transmitter has 3 masts: 2 with a height of 120 metres used for broadcasting on 1422 kHz and a 50 metres high mast used for broadcasting on 1179 kHz.
The 50 metres high mast and the western 120 metres high mast are insulated against ground. The eastern 120 metres high mast was also insulated, but is now grounded and equipped with a cage antenna.
| Harald||2014-07-08 13:44:40|
800 x 534, 547 кБDamaged pole of a 380 V - line south of Bretten, Germany
| Harald||2014-07-07 13:03:00|
800 x 600, 910 кБPylon 110 of Hoheneck-Herbertingen powerline
| Harald||2014-07-07 12:54:58|
800 x 1067, 1503 кБPhase markings on the other site of pylon 110 of Hoheneck-Herbertingen powerline
| Harald||2014-07-07 12:48:16|
800 x 1067, 1500 кБPhase marking at pylon 110 of Hoheneck-Herbertingen powerline
| Harald||2014-07-07 12:38:14|
800 x 1200, 1277 кБPhases of Hoheneck-Herbertingen Powerline. The phases of the 220 kV circuit are marked yellow, that of the 380 kV circuit red
| Harald||2014-06-30 12:36:35|
800 x 1200, 1237 кБClose view at the termination tower
| Harald||2014-06-30 12:27:06|
800 x 1200, 1262 кБCloser view at the second tower
| Harald||2014-06-30 11:52:19|
800 x 1200, 1133 кБCloser look at one of the abandoned 20 kV-pylons at Böblingen
| Harald||2014-06-28 19:46:19|
800 x 534, 587 кБ2 abandoned lattice towers, which were until recently used by a 20 kV-line, which is now undergrounded, near Böblingen, Germany
| Konstantin||2014-06-24 16:16:36|
800 x 1107, 75 кБКВЛ 110 кВ "Заостровка", г. Пермь. Анкерно-угловая многогранная 4-х цепная опора для угла 45˚ с высотой подвеса нижнего провода 17,5 м.